Open pressure relief valve troubleshooting is triggered because the compressor operates at excessive pressure and there is damage to the valve. If you want to fix this, adjust the pressure level in Intellisys control and replace the damaged valve. On the other hand, if your company has a lot of slightly damaged ball screws, then perhaps you want to call the best repair chipboard screw holes company to repair them for you.
In addition, your screw compressor may often turn itself off. There are many causes for compressors to shut down by themselves, including too high an inlet temperature, too low pressure in the separator, a damaged pressure sensor or temperature sensor, and a 1SL starter failure (2SL).
If this condition occurs, check the ventilation and make sure the compressor is inadequate ventilation. Even better if cooling the compressor room using AC (Air Conditioner). Also, check the cooling fan and make sure it is still operating properly. Check the cooler core and clean it if the cooler core is dirty.
Whereas to handle the separator pressure is low, check the possibility of an air leak from the blowdown pipe and tank. Also, add pressure in the separator. Perform an inspection of the sensor and the possibility of a faulty sensor cable or poor sensor connection. Meanwhile, if the cause of failure is starter 1 SL (2SL), then do a cable check. Usually, there are broken or lose cables.
Finally, overheating occurs when the working temperature of the system exceeds 1000C in the compressor screw, which is usually caused by poor circulation in the compressor room, no oil replacement, oil separator blockage, inhibition of heat dissipation in the unit cooler, blockage of oil filters and malfunctioning distribution mechanism in the oil filter housing unit. If there is a problem like this, then the action that can be taken is to immediately check and resolve the problem that caused it.